Replacement of Cooling Towers - 2 nos (4 Cell)Services
Scope of Work: Replacement of Cooling towers at DEC Tower (Building 1 and Building 2)- 4 cells (3+1)
Inlet Water Temp: 103 F
Outlet Water Temp: 93 F
Wetbulb Temp: 87.8 F
Total Flow rate per building: 1,969.6 USGPM
Material: Stainless Steel Or FRP + Stainless Steel
- CTI Certified Cooling towers
- Dismantle and replace existing cooling towers with new cooling tower.(including mechanical components and fills)
- Install VFDs with panels and programming of same for all Cooling tower motors.
- Replace the existing cables and cable trays from panel to Cooling towers.
- Replace the header pipe supports.
- Modification of pipeline as per new CT selection.
- Anti-corrosive painting of cooling tower pipe lines (rooftop only)
- Modification of foundation as per new CT selection.
- Replacement of valve package (inlet, outlet, equalizer line etc).
Terms & Condition
DEC Towers Jointly Owned PropertyMixed Use
Dec Towers Dubai Marina, Dubai, United Arab Emirates